How to configure 6 tons of reverse osmosis host? How to do the graduation design of the water treatment project, the topic I did is water treatment, the original water treatment into pure water, secondary reverse osmosis can be. at present, there is no clue. I hope the master can provide me with a catalogue. it is better to have the format of the whole paper. and general direction of thinking. or learn from the information. detailed points !! The process flow of this level 2 RO system of 10 tons, the original water tank, →, the original water pump, →, quartz sand filter, →, activated carbon filter, → scale and scale dosing system →, precision filter, →, reverse osmosis, →, secondary reverse osmosis, →, pure water tank, →, pure water pump, →, sterilization system →, water point, Process Description 1. original water tank: the function of the original water tank is to store raw water, provide stable water source for follow-up equipment. The system has 1 original water tank with a volume of 10m3 and PE material.
Can the water after coagulation be removed with a 150um filter? What you are talking about should be the sedimentation or floating objects after coagulation. the accuracy of 150 microns is very low. the accuracy of 1 micron cannot remove the turbidity of water, let alone 150 microns. it can be used with a folding filter element of 0.1 microns, the effect is more ideal and the amount of water is large. there are 5-inch 10-inch 20-inch 30-inch 40-inch security filters available, which are folded in the filter element and played by pure hands.